The Flexible Space underfloor air conditioning system offers two options to distribute the conditioned air into the work space, either via a recessed Fantile, or via a floor standing air terminal unit.
Each unit contains twin scroll fans driven from a single motor, an open/shut control damper and integrated control unit (Fatronic) which dictates the air flow. Air terminals can work independently or connected in a network
Fantiles are designed to replace a standard 600 mm x 600 mm floor panel and the modular design makes it easy to relocate them if layout changes are required.
Recessed Floor Terminal Units
TU4-AC | TU4-EC: Standard Model that requires a minimum 215 mm clearance within the floor void
TU350: Slimline Model that requires a minimum 180 mm clearance within the floor void
Console Terminal Unit
TUC500: Floor standing option for areas unsuitable for recessed floor terminals. The unit is located over an opening in one floor tile.
Functions of Terminal Units
Temperature Control: Two sensors located in the terminal read room and under floor air temperatures
Automatic Summer/Winter changeover: independent from the CAM unit
Regulation of Setpoint: the room temperature required can be set by the user
Fan Speed Modulation: Select different fan speeds or lock the fan at a fixed speed
Alarm: Automatic diagnostics where the control activates fan switch-off and isolate the terminal indicating the fault on the display
Master and Slave: Terminal units can be designated as Master or Slave allowing control to be regulated
Electronic Heater Control: A delay can be set between fan actuation and electrical heater activation to ensure greater energy efficiency and avoid current peaks caused by simultaneous start up